Carbon Monoxide Alarms Are Recalled! – Maple Chase
WASHINGTON, D.C. - The U.S. Consumer Product Safety Commission, in cooperation with the firm named below, today announced a voluntary recall of the following consumer product. Consumers should stop using recalled products immediately unless otherwise instructed.
Name of Product: FireX Branded 10000 Series Carbon Monoxide (CO) Alarms and 12000 Series CO/Smoke Combo Alarms
Units: About 280,000
Manufacturer: Maple Chase Company, of Plain City, Ohio
Hazard: The recalled alarms can sound a “double chirp”/fault alarm in the presence of CO, prior to going into full alarm. Upon hearing a double chirp, the Owner’s Manual instructions recommend a consumer take the alarm out of service, which could expose consumers to hazardous levels of CO and suffer injury or death.
Incidents/Injuries: None reported.
Description: The recall includes FireX branded 10000 and 12000 series alarms with item numbers: 10000, 12000, 12000C, 12000-6, 12200, 12220, 12400, 12400C manufactured between June 1, 2007 and February 1, 2008. The date code appears on the back of the unit with a four digit year, three digit month followed by the day (ex: 2007JUN1 for June 1, 2007). Units with a manufacture date code prior to June 1, 2007 are not included in this recall.
Sold: Commercial electrical distributors and electrical contractors and builders for installation into new home construction. A limited number of units were sold at Menard’s nationwide from June 2007 through February 2008 for about $20 (10000 series) and $30 (12000 series).
Manufactured in: Mexico
Remedy: Consumers should contact Maple Chase immediately to receive a free comparable replacement alarm and make arrangements to return their recalled alarms. Consumers should not take the alarms out of service until they receive the replacement alarm.
Consumer Contact: For more information, contact Maple Chase toll-free at (888) 879-3906 between 8 a.m. and 6 p.m. CT Monday through Friday or go to the firm’s Web site at www.firexsafety.com